Our Klamath Basin Water Crisis
Upholding rural Americans' rights to grow food,
own property, and caretake our wildlife and natural resources.
Notice of a Completeness Determination on An
April 30, 2003
Peoples Energy Resources Corp, under the subsidiary name of COB Energy Facility, LLC ("COB"), has submitted an application for a site certificate ("ASC") to build the COB Energy Facility ("project"), a natural gas-fired, combustion turbine, combined-cycle energy facility in Klamath County near Bonanza, Oregon. The Oregon Office of Energy ("Office") has determined that the application is complete and filed it on April 30, 2003. The Office now is ready to begin the substantive review of the application.
The Office gives this notice pursuant to OAR 345-015-0190. Pursuant to ORS 469.320, COB may not construct the energy facility without the Oregon Energy Facility Siting Council ("Council") approving a site certificate.
Within a few weeks, the Office will issue public notice about an information meeting we will hold in the Bonanza area to discuss the contents of the application. We will also advertise the meeting in the Klamath Falls Herald and News. This information meeting is not the same as the public hearing that will occur once the Office issues a draft proposed order on the application. The information meeting is for discussion purposes only.
Description of the Proposed Facility. The proposed project would have a nominal generating capacity of 1150 megawatts ("MW"). The energy facility site would consist of four essentially identical combustion turbine generators, four heat recovery steam generators, and two steam turbine generators. The project would also include a nearby 51.2-acre wastewater evaporation pond and a 21.4-acre water supply reservoir. Other facilities include an administration/control room building, warehouse/maintenance building, parking area, water treatment building, raw water and demineralized water storage tanks, stormwater detention pond, switchyard, septic tank/leach field, gas metering and regulation station, and cooling towers.
Most of the structures at the energy facility site would be shorter than 100 feet. The tallest structures would be four stacks that are about 150 to 200 feet high.
The project would require an average of 5,390 gallons of water per minute and a maximum of 7,590 gallons per minute. The project has applied for a water use permit to use 16.7 cubic feet of water per second for industrial use and 0.2 cubic feet per second for irrigation of 16 acres. The source of water would be three deep wells in the Lost River Basin. The wells would be located about 2.8 miles east of the energy facility site. As part of the ASC process, the Council will make the decision on whether the Department of Water Resources should issue the water use permit for the project.
Natural gas from the existing PG&E GTN system at the Bonanza Compressor Station would serve the project. The project proposes an approximate 4.1-mile-long, 20-inch-diameter natural gas pipeline to connect the proposed energy facility site with one or both of the existing pipelines at the compressor station.
The project would deliver electric power to the regional power grid at the Bonneville Power Administrationís ("BPA") Captain Jack Substation. To do so, COB proposes to build a new 500-kV alternating current transmission line about 7.2 miles long. The transmission line would consist of about 38 transmission towers ranging in height from 100 to 165 feet.
Location of the Proposed Facility. The proposed project site is located about three miles south of the city of Bonanza on the east side of West Langell Valley road in Klamath County, Oregon. Most of the projectís components would be located at this site on 136.7 acres within a 749-acre parcel that COB would own. Access to this proposed site would be from West Langell Valley Road. Additional related or supporting facilities would bring the proposed total acreage to 194.3.
Transmission line Route
The proposed transmission line would consist of about 38 transmission towers ranging in height from 100 to 165 feet. The proposed route would be within a 154-foot wide corridor. The proposed route first crosses West Langell Valley Road, then crosses over the north end of Bryant Mountain and then runs south along the western flank of Bryant Mountain to the Captain Jack Substation. The project would need to acquire a new right-of-way for the transmission line corridor to the Captain Jack Substation. Negotiation of easements for the right-of-way is a private matter between COB and the property owners and is not part of the Council review. However, the 7.2-mile-long electric transmission line would be a related or supporting facility under the Councilís jurisdiction.
Natural Gas Pipeline Route
COB proposes to build a 20-inch-diameter natural gas pipeline about 4.1 miles long to connect the proposed energy facility site with one or both of the existing pipelines at the compressor station. The pipeline is proposed to run along the right-of-way of existing Klamath County roads from the compressor station to the proposed energy facility site. The 4.1-mile-long pipeline would be a related or supporting facility under the Councilís jurisdiction.
Water Pipeline Route and Water Storage Pond
The project would pump water from the proposed well site through a 20-inch pipe. The water pipeline would run across the southern end of "Dead Indian Hill," through land the applicant will own to a water supply reservoir occupying about 21.4 acres and sized to hold about 64 million gallons. The water supply reservoir would be located just northwest of the energy facility site. A 24-inch pipe would carry water about 2,300 feet from the water supply reservoir to the energy facility. The 2,300-foot-long pipeline and the water storage pond would be related or supporting facilities under the Councilís jurisdiction.
Wastewater Pipeline and Evaporation Pond
Wastewater from the project would be discharged as a solids stream and a wastewater stream into a 51.2-acre wastewater evaporation pond located just southeast of the energy facility site. Evaporation from the pond would leave a solid sludge that would be removed for disposal in a licensed landfill. A 4-inch pipeline would carry wastewater from the energy facility to the evaporation pond. A 2-inch pipeline would do the same for the solids stream. Each pipeline is about 2,000 feet long. No off-site wastewater discharge is proposed.
The 2,000-foot-long pipelines and the evaporation pond would be related or supporting facilities under the Councilís jurisdiction. The evaporation pond would need a Water Pollution Control Facilities ("WPCF") permit from DEQ. As part of the ASC process, the Council will make the decision on whether DEQ should issue the WPCF for the project.
The project would dispose of sanitary sewage through an on-site septic tank system, for which it would also need a Water Pollution Control Facilities ("WPCF") permit from DEQ. As part of the ASC process, the Council will make the decision on whether DEQ should issue the WPCF for the project.
Removal-Fill Permit. At this time, the project does not appear to require a Removal-Fill permit from the Division of State Lands ("DSL"). If a Removal-Fill permit should be needed, the Council will make the decision on whether DSL should issue the Removal-Fill permit for the project as part of the ASC process.
Land Use. The project proposes to occupy 194.3 acres. Surface components occupying land include:
The project proposes to use about 161 acres zoned for Exclusive Farm Use and about 33 acres zoned for Forestry. The project would require an exception from Goal 3 of the State of Oregonís statewide planning goals. The Councilís rules for evaluating a Goal 3 exception can be found at ORS 469.504(2).
Land Use Approval. Pursuant to OAR 345-022-0030(2)(b), the Council will review the proposed facility to determine whether it complies with Klamath Countyís land use and zoning ordinances as well as with state land-use laws. People who wish to comment on land use issues may direct their comments to the Office during its review of the application. For the Council to consider public comments later in the proceeding, people must make comments during the public hearing on the draft proposed order, as explained below. The Council has appointed the Klamath County Board of Commissioners to a Special Advisory Committee to assist it in its review of land use and other issues.
Anticipated Significant Impacts of Construction and Operation of the Facility. The facility must meet the State of Oregonís standards for environmental impact.
Review Schedule for the Application. The Council, with assistance from the Office, will review the application for compliance with applicable state standards.
Public and Other Governmental Agenciesí Comments on ASC. The Office welcomes comments from the public and other governmental agencies on the ASC as it prepares its Draft Proposed Order. Please submit comments on the ASC to the Office at the address below by June 23, 2003.
Draft Proposed Order. The Office will review the application. As part of its review, it will consider comments and regulations from other state and local agencies and tribes, as well as comments from the public. It will prepare a draft proposed order, which will recommend that the Council either approve or deny the application. The draft proposed order will include findings of fact, conclusions of law, and recommendations. If it recommends that the Council approve the application, the Office will include recommended conditions for the energy facility site certificate.
Public Hearing. The Office will schedule a public hearing after it releases the draft proposed order. The Office will hold the hearing in the vicinity of the project, probably in the Bonanza area. It will notify affected property owners, people on its special mailing list for the project, and all people on the Councilís general mailing list about the public hearing. It will also publish a notice in the local newspapers. The notice will also state where members of the public can view the draft proposed order.
The public hearing is an important meeting. Any comments made at the public hearing will be part of the decision record for this application. The public hearing is an informational hearing, not a contested case hearing. A person must comment in person or in writing on the record of the public hearing to preserve the right to participate in a contested case proceeding as a party or a limited party. A person must raise an issue specifically enough that the Council, the Office, and the applicant have an adequate opportunity to respond. A personís comments must relate to an issue about which the Council has authority to act. A person must comment at this stage also in order to preserve the right to appeal the Councilís final decision.
Proposed Order. Following the public hearing on the draft proposed order, the Council will review the draft proposed order. The Council does not permit public comment during this review, although the review will take place during a regular Council meeting.
Following the Councilís review, the Office will issue a proposed order. In doing so, it will take into account comments of the Council, testimony at the public hearing, written comments it received in a timely manner, and agency consultations. In the proposed order, the Office will recommend that the Council either grant a site certificate with conditions or deny the application. The Office will notify the public when it issues the proposed order.
Opportunity for a Contested Case. The Council will appoint an independent hearing officer to conduct the contested case proceeding. Following issuance of a proposed order by the Office, the Office will issue a contested case notice.
Only the applicant, the Office, and those who have participated in and raised issues in the public hearing and have been admitted as parties by the hearing officer may participate in the contested case. Once the contested case process begins, there are no further opportunities for comments from the general public.
Council Decision. Following the contested case hearing, the hearing officer will provide a written recommended order to the Council. The Council will consider the proposed order, the hearing officerís recommended order and any partiesí exceptions to the order. The Council will decide whether or not to issue a site certificate and any conditions of approval.
Reconsideration and Appeal. Following the decision and final order, any party to the contested case has 30 days following the date of service to petition for a rehearing. In addition, a party may file a petition for judicial review within 60 days from the date of service of the Council's final order or within 30 days after the date a petition for rehearing is denied. Judicial review of the Councilís decision is directly to the Oregon Supreme Court.
Copies of the Application. The public may review copies of the "Application for a Site Certificate for the COB Energy Facility" at the public libraries in Klamath Falls, Bonanza and Bly. Their addresses are:
Klamath County Library Bonanza Branch Library Bly Branch Library
126 S. 3rd St. 31703 Highway 70 366 Elder St.
Klamath Falls, OR 97601 Bonanza, OR 97623 Bly, OR 97622
To Submit Comments or to Request Further Information. The Oregon Office of Energy contact for the project is:
Catherine Van Horn
Energy Facility Analyst
Oregon Office of Energy
625 NE Marion Street
Salem, OR 97301-3737
503.378.4041 or 800.221.8035 (toll-free in Oregon)
You can find more information about the Oregon energy facility siting process at www.energy.state.or.us/siting/sitehm.htm.
Page Updated: Saturday February 25, 2012 05:23 AM Pacific
Copyright © klamathbasincrisis.org, 2001, All Rights Reserved